Technical information about your connection
Preferably contact us when your building plans are ready. We will then discuss which connection is the most suitable, where the network connection should go in your building and which works will be necessary.
The network connection point is the element connecting your location with the Telenet network with a connection cable.
There are connection points with two, four and eight outputs. These are located:
The connection cable linking your location with the network connection point must meet certain requirements. The type of connection cable you need depends on the distance between the network connection point and your basic configuration.
In that case, use the table of cable types to determine which cable you need. Use a conduit with a 40 mm diameter to lay the section of cable on your premises.
Caution! If the cables are more than 80 m long, a special connection is required. Please contact us if that is the case.
|Type of connection cable|
|Required length||0 – 30 m||31 – 50 m||51 – 80 m||> 80 m|
|Type of cable to be purchased
|PE6||PE11||PE14||Please contact us|
This is possible in buildings with 9 or more individual connections. In that case, we will handle the installation of the connection cable. You or the building’s owner will be responsible for laying a conduit between the cable on the road and the first connection point in your building. This conduit must have a 125 mm diameter and be installed 60 cm deep. Make sure to contact us first.
A Telenet installer will put in place the basic configuration in your building. The basic configuration is linked to the network connection point with the connection cable. The indoor cabling starts from the basic configuration.
The minimum basic configuration consists of:
The basic configuration is fitted on to a wooden panel of at least 50 by 50 cm and 1.8 cm thick. This panel is installed by you. You can make the panel bigger for future expansion of the basic configuration with switches or other equipment. Also provide at least 4 earthed 230 V power points. Fit the panel at eye level in a dry technical area.
The indoor cabling must be installed by you or a contractor of your choice. It always starts from the basic configuration. Preferably choose built-in cabling with all cables and sockets in the wall. Do not start your indoor cabling until you are certain of the location of your basic configuration.
You are responsible for purchasing the materials for the indoor installation. Always use the correct approved materials.
|UTP category 5E||UTP category 5E||PVC6 coaxial cable|
SocketsSocket (Telenet-Interkabel certified)
|RJ-11 or RJ-45||RJ-45||TV/FM|
Connection cable for the deviceConnection cable (Telenet-Interkabel certified)
|UTP category 5E with RJ-11||UTP category 5E with RJ-45||TV/FM|
Telenet has specific solutions for the distribution of digital television in large buildings such as hospitals and hotels. Please ask your Account Manager for more information.